The following are recommendation for installation proportional injectors: Aquablend, Chemilizer, Microdos, Minidos and Superdos.
REQUIRED!!: For every installion it is required to use a sediment filter (min 104 microns), not using such filter will void your warranty
RECOMMENED: the use of slow open/close ball vales, pressure regulator before pump and reverse valve after pump. These items are recommended for safety reasons and help with prevention of water hammer and high pressure spikes.
It is very important when opening and closing water flow to do it in a slow manner. When opening water flow please let pump "click" regularly then open water flow
Due to the nature of electric solenoids closing water flow very fast it's very important to provide additional safety measure in protecting pump from water hammer.
If yo have any questions regarding installation, please contact us and we'll be happy to help or answer any questions you might have.
CORRECT WAY OF TURNING ON WATER FLOW IN A INSTALLATION WITH BY-PASS
In order for water not to flow to the pump, close valves (B) and (C)
Open valve (A)
SLOWLY open water flow
In order to bleed out air in the installation, open all valves after by-pass installation
SLOWLY open valve (B)
Open valve (C) and then close valve (A)
To close the installation, please follow above instruction in reverse order